Common oil water separator problems and their solutions
Oil water separators are important pieces of equipment for managing wastewater from industrial sites. They help companies remain compliant with regulators and protect the environment from pollution. However, like any piece of equipment, they must be cared for to ensure that they are operating as per design.
The worst case scenario is that you only find out something is wrong with your oil water separator when you have a release of out-of-specification water from your facility. To prevent this, here are some of the things you need to check regularly in order to ensure your oil water separator keeps performing as intended.
If you need specific advice on oil water separators as well as maintenance and troubleshooting, the team at Cleanawater can help.
Common problems and solutions for vertical gravity and coalescing plate separators
Water is not flowing, or there is a low flow into the oil water separator
A low water flow could indicate a problem with the pump, sump level or the suction line. Some of these issues are common to any kind of separator. For details on how to check these systems, refer to this article that addresses hydrocyclone separators too.
Take these steps to clear the suction line of a gravity or coalescing separator:
Clear obstructions by flushing
Repair cracks or loose fittings that allow air into the system
Clear foot valve from obstructions.
Water is flowing into the waste oil container, or water is flowing out of the top of the separator
The waste oil collar inside the unit may be set too low. The collar should be set to five millimetres above the water level when the pump is running to prevent free water from being skimmed off with the waste oil.
Look for a discharge blockage. Check media packs, and clean as necessary. Regular blockages may need further investigation into the unit sizing and removal of solid debris.
The pump may be rated too high. Excess flow rate through the unit negatively affects its performance.
There is no oil in the waste oil container
The waste collar inside the unit may be set too high. The collar should be set to five millimetres above the water level when the pump is running to ensure that oil is removed from the system and does not build up inside the separator.
The waste water stream is clean and therefore no oil is being collected. No action required.
Oils have formed an emulsion in the waste water stream and cannot be removed by a coalescing or vertical gravity separator. Make sure no unapproved degreasers and detergents are being used in the system. Contact Cleanawater for technical support to handle emulsions.
The pump overload keeps tripping and system switching on/off issues
Problems related to switching the equipment on or off are usually related to electrical or control panel issues. These and pump overload checks are described in more detail in our article for hydrocyclone oil separators. Read more about these issues.
There is oil present in the water discharge
There are 3 potential causes of oil being carried over to the water outlet stream. Firstly, an oil spill may have overloaded the system. Secondly, the waste oil decant tank may be full. Thirdly, there may be a formation of emulsions which would require investigation by Cleanawater experts. Finally, check media packs and clean as per operations and maintenance schedule.
There is a smell coming from the oil water separator
Check all basic operating conditions as you would for a hydrocyclone separator – read more here. If the problem persists, arrange for servicing of the unit by Cleanawater technical experts.
Contact Cleanawater for more information about troubleshooting your oil water separator
Expert advice and technical support are close at hand with Cleanawater. Our qualified technicians are experienced in working on all types of oil water separators in a variety of industries. We can assist you to diagnose problems and provide solutions to resolve them.
We will help you ensure your business remains compliant with all water authority regulations. From design and installation to support and maintenance, we're the oil water separator experts.
Cleanawater on 2 September 2021
No matter what industry you’re in, chances are you need odour control. VapourGard can help you eliminate odour complaints in a safe, cost-effective, and versatile way. ...Read more